Oatey® 1.5 in. NPT Chrome In-Line Vent
The Oatey® 1.5" NPT Chrome In-Line Vent replaces secondary plumbing vents that protect the traps in kitchens and bathrooms. This mechanical vent installs on the drain line and vents the line without allowing sewer gas to enter the home. Oatey products have earned the trust of plumbing professionals for over 100 years.
Part #: 39000
- For venting sinks, tubs, showers
- Constructed of ABS
- Helps prevent sewer gas from entering the home
- Spring-loaded to open with negative pressure and close with positive pressure
- NSF-24 listing for use in recreational vehicles
- Available in chrome
- Push to connect
- For warranty product details, refer to the Oatey Limited Warranty document
|Connection Size:||1.5 in.|
|DFU Rating:||20 Branch, 8 Stack|
Yes. Any AAV can malfunction or not operate properly because it is a mechanical device. Signs of that the Sure-Vent is not operating as intended, are foul odors. If you smell foul odors (sewer smell) near a plumbing fixture which has a Sure-Vent installed, this means the Sure-Vent is not closing properly to create a positive seal and should be replaced. Some individuals relate slow drains to the Sure-Vent not operating properly. The Sure-Vent is not the issue, the slow drain is related to a partial blockage within the drain itself. A partially blocked drain will fill with water when the fixture is draining, and the Sure-Vent recognizes the positive pressure from the restriction and stays in closed position to stop backflow out of the Sure-Vent. You should have your drain cleaned when this occurs.
Can the Sure-Vent be used to vent a sealed sump pit with waste grinder pump?
Yes, with exceptions. Always check with your local building officials to confirm this application is approved in your municipality before attempting this installation. We also recommend that you check with the pump manufacture before completing this installation. Remember that you also need to vent any fixture or group of fixtures, check with your local building official to ensure your plumbing system is designed properly before installation. If they are not vented properly the drains will not flow properly. After confirming all parties involved approve this application, you can contact our customer service department and they will be happy to send out a drawing explaining the application.
What is the definition of an AAV?
AAV = Air Admittance Valve.